Remove the need to install the protective cover, in order to ensure the large span cable bridge in Ji'nan to play the greatest effect, but also need to pay attention in wiring.
If the installation site is corrosive or very humid environment, the wiring must be based on the different corrosion media to take appropriate protective measures.
If the sets of Ji'nan cable tray in the same height of smooth installation, we need to consider the maintenance and overhaul of Ji'nan cable bridge the distance between the groups.
In the large span cable bridge on Ji'nan can be gapless cable, power cable cross-section in the bridge filling rate to below 40%, while the control cable should be less than half of the cross-sectional area of the bridge.
When the installation of large span cable bridge in Ji'nan cannot be installed above the corrosive gas pipeline and heating pipelines, under corrosive liquids pipeline cannot be directly installed in Ji'nan cable tray, so it must be if it should do the protection and insulation measures.
Your satisfaction is our pursuit, let us join hands in creating a better tomorrow in twenty-first Century! Our company will be as in the past cherished customers love and trust, the pursuit of perfect quality of service forever, let customer satisfaction report writing.